TY - JOUR
T1 - A Bayesian Network model for predicting cooling load of commercial buildings
JF - Building Simulation
Y1 - 2018/02//
SP - 87
EP - 101
A1 - Sen Huang
A1 - Wangda Zuo
A1 - Michael D. Sohn
KW - Bayesian Network model
KW - cooling load prediction
KW - training dataset
KW - Uncertainties
AB - Cooling load prediction is indispensable to many building energy saving strategies. In this paper, we proposed a new method for predicting the cooling load of commercial buildings. The proposed approach employs a Bayesian Network model to relate the cooling load to outdoor weather conditions and internal building activities. The proposed method is computationally efficient and implementable for use in real buildings, as it does not involve sophisticated mathematical theories. In this paper, we described the proposed method and demonstrated its use via a case study. In this case study, we considered three candidate models for cooling load prediction and they are the proposed Bayesian Network model, a Support Vector Machine model, and an Artificial Neural Network model. We trained the three models with fourteen different training data datasets, each of which had varying amounts and quality of data that were sampled on-site. The prediction results for a testing week shows that the Bayesian Network model achieves similar accuracy as the Support Vector Machine model but better accuracy than the Artificial Neural Network model. Notable in this comparison is that the training process of the Bayesian Network model is fifty-eight times faster than that of the Artificial Neural Network model. The results also suggest that all three models will have much larger prediction deviations if the testing data points are not covered by the training dataset for the studied case (The maximum absolute deviation of the predictions that are not covered by the training dataset can be up to seven times larger than that of the predictions covered by the training dataset). In addition, we also found the uncertainties in the weather forecast significantly affected the accuracy of the cooling load prediction for the studied case and the Support Vector Machine model was more sensitive to those uncertainties than the other two models.
VL - 11
IS - 1
JO - Build. Simul.
ER -
TY - JOUR
T1 - A Bayesian network model for the optimization of a chiller plant’s condenser water set point
JF - Journal of Building Performance Simulation
Y1 - 2018/12//
SP - 36
EP - 47
A1 - Sen Huang
A1 - Ana Carolina Laurini Malara
A1 - Wangda Zuo
A1 - Michael D. Sohn
KW - Bayesian network
KW - Condenser water set point
KW - modelica
KW - regression-based optimization
AB - To implement the condenser water set point optimization, one can employ a regression model. However, existing regression-based methods have difficulties to handle non-linear chiller plant behaviour. To address this problem, we develop a Bayesian network model and compare it to both a linear and a polynomial regression model via a case study. The results show that the Bayesian network model can predict the optimal condenser water set points with a lower root mean square deviation for both a mild month and a summer month than the linear and the polynomial models. The energy-saving ratios by the Bayesian network model are 25.92% and 1.39% for the mild month and the summer month, respectively. As a comparison, the energy-saving ratios by the linear and the polynomial models are less than 19.00% for the mild month and even lead to more energy consumption in the summer month (up to 3.73%).
VL - 11
IS - 1
JO - Journal of Building Performance Simulation
ER -
TY - JOUR
T1 - Improved cooling tower control of legacy chiller plants by optimizing the condenser water set point
JF - Building and Environment
Y1 - 2017/01//
SP - 33
EP - 46
A1 - Sen Huang
A1 - Wangda Zuo
A1 - Michael D. Sohn
KW - Condenser water set point
KW - Model predictive control
KW - modelica
KW - Optimization frequency
KW - Optimization starting point
AB - Achieving the optimal control of cooling towers is critical to the energy-efficient operation of current or legacy chiller plants. Although many promising control methods have been proposed, limitations in their applications exist for legacy chiller plants. For example, some methods require the change of the plant's overall control structure, which can be difficult to legacy chiller plants; some methods are too complicated and computationally intensive to implement in old building control systems. To address the above issues, we develop an operational support system. This system employs a model predictive control scheme to optimize the condenser water set point and can be applied in chiller plants without changes in the control structure. To further facilitate the implementation, we propose to increase the optimization accuracy by selecting a better starting point. The results from a case study with a real legacy chiller plant in Washington D.C. show that the proposed operational support system can achieve up to around 9.67% annual energy consumption savings for chillers and cooling towers. The results also show the proposed starting point selection method can achieve a better accuracy and a faster computational speed than commonly used methods. In addition, we find that we can select a lower optimization frequency for the studied case since the impact of the optimization frequency on the energy savings is not significant while a lower optimization frequency does reduce the computational demand to a great extent.
VL - 111
JO - Building and Environment
ER -
TY - JOUR
T1 - Amelioration of the cooling load based chiller sequencing control
JF - Applied Energy
Y1 - 2016/04//
SP - 204
EP - 215
A1 - Sen Huang
A1 - Wangda Zuo
A1 - Michael D. Sohn
KW - Chiller sequencing control
KW - Model-based optimization
KW - Multiple-chiller plant
AB - Cooling Load based Control (CLC) for the chiller sequencing is a commonly used control strategy for multiple-chiller plants. To improve the energy efficiency of these chiller plants, researchers proposed various CLC optimization approaches, which can be divided into two groups: studies to optimize the load distribution and studies to identify the optimal number of operating chillers. However, both groups have their own deficiencies and do not consider the impact of each other. This paper aims to improve the CLC by proposing three new approaches. The first optimizes the load distribution by adjusting the critical points for the chiller staging, which is easier to be implemented than existing approaches. In addition, by considering the impact of the load distribution on the cooling tower energy consumption and the pump energy consumption, this approach can achieve a better energy saving. The second optimizes the number of operating chillers by modulating the critical points and the condenser water set point in order to achieve the minimal energy consumption of the entire chiller plant that may not be guaranteed by existing approaches. The third combines the first two approaches to provide a holistic solution. The proposed three approaches were evaluated via a case study. The results show that the total energy consumption saving for the studied chiller plant is 0.5%, 5.3% and 5.6% by the three approaches, respectively. An energy saving of 4.9–11.8% can be achieved for the chillers at the cost of more energy consumption by the cooling towers (increases of 5.8–43.8%). The pumps’ energy saving varies from −8.6% to 2.0%, depending on the approach.
VL - 168
JO - Applied Energy
ER -